Copper Tube Medical Gas ASTM B Type K Specification including outside diameter, wall thickness and weight. This standard is issued under the fixed designation B ; the number 1 This specification is under the jurisdiction of ASTM Committee B05 on Copper. 10 Sep This specification establishes the requirements for two wall thickness schedules of specially cleaned, straight lengths of seamless copper.
|Published (Last):||22 August 2011|
|PDF File Size:||6.43 Mb|
|ePub File Size:||9.42 Mb|
|Price:||Free* [*Free Regsitration Required]|
Referenced Documents purchase separately The documents listed below are referenced ashm the subject standard astm b819 are not provided as part of the standard. The values given in parentheses are mathematical conversions to SI units, which are provided for information only and are not considered standard.
It is the responsibility of the user of astm b819 standard to establish appropriate safety, health, and environmental practices and determine the applicability of regulatory limitations prior to use.
Types K and L tube are defined astm b819 Specification B It is not a specification for the various types and alloys. Notes are optional and private.
C seamless pipe in standard pipe sizes, both regular and extra strong, and seamless tube in straight lengths astm b819 general engineering purposes. Related Products Searching for related products It is informational only and not an official part of astm b819 standard; the full text of the standard itself must be referred to for its use and application.
Related Suppliers Searching for related suppliers The tube shall be installed in conformance with astm b819 requirements of the National Fire Link to Adtm This link will always route to the current Active version of the standard. The values given ashm parentheses are mathematical conversions to SI units that are provided for information only and are not considered standard. Seamless copper tube for medical gas systems shall be furnished in the H58 Drawn General Purpose temper. Drawn temper tube is suitable for astk with capillary solder joint astm b819 for brazing.
The product shall be manufactured by such hot working necessary to convert astm b819 billet to a tubular shape and cold worked to the b189 size. Historical Astm b819 s – view previous versions of standard. The tubes are used in surface condensers, evaporator Astm b819 is the responsibility of the user of this standard to establish appropriate safety and health practices and determine the applicability of regulatory limitations prior to use.
ASTM B – 18 Standard Specification for Seamless Copper Tube for Medical Gas Systems
This standard does not purport to address all of the safety concerns, if any, associated with its use. This abstract is a brief summary of the referenced standard. You have successfully saved to your supplier list. The tube shall be installed in conformance with the requirements of th This standard does not purport to address all of the safety concerns, if any, associated asttm its use.
The tubes used for medical gas systems shall be cleaned by any of the astm b819 recommended methods: ASTM does not give any warranty express or implied or make any representation that the contents of this abstract are accurate, complete or up to date. Note Drawn temper astm b819 is suitable for use with capillary solder joint fittings for astm b819.
Work Item s – proposed revisions of this standard. Eddy-current test, a nondestructive test, astm b819 astj performed as well. This specification establishes the requirements astm b819 two wall thickness schedules of specially cleaned, straight lengths of seamless copper tube, identified as Types K and L, suitable for medical gas systems.
Tension test and Rockwell hardness test shall be performed to determine the tube’s tensile strength and hardness, respectively.